Hello Phoenix Multiplus 12/1600/70 started to cut out on AC in 'charger only' setting connected to shore line. It started intermittently and I assumed it was voltage drop from shore post changed cables & input but no issues. The green light comes on for inverter and 230V sockets work from that but as soon as 16A shore plug is connected fan comes on then orange charging light briefly then relay clicks and shuts down the red thermo fuse no doesn't pop out???
I have 4x sealed Hankook 12v leisure DC batteries along with 600w solar to a 50A MPPT charge controller which was doing fine for 4+ years only recently with addition of 2x 500w smart radiators being installed if they were on at same time as fan oven the Multiplus fuse would pop out then reset when pushed back in. A guest on boat confessed to using an electric kettle which may of pushed past 1600w limit of the Victron could this of broken charger? The inverter still works I have tried pushing up the AC plug connectors to ensure a good connection anything else I can try internal fuse replacement?
Thanks in advance
I have an old 2001 Phoenix combi and i want to turn the ground relay off to suit UK equiptment.
I have a mk3 to usb and i have tried plugging that into the combi unit to access through ve configure but it dosent seem to want to connect. I presume the unit is too old. Is there another way to do this?
I want to connect my Cerbo GX to the NMEA2000 network using the VE.CAN->NMEA2000 cable (ASS030520200). Would it then be possible to control the relays of the CerboGX via the NMEA2000 network (i.e. via CZone) ?
Would it also be possible to read out the binary-inputs of the Cerbo GX via the NMEA2000 network?
My inverter is on charger only mode currently, with grid power connected to ac-in 1 and pass through to ac out, but the inverter will still randomly disconnect the grid power from my house. What is the possible cause for this problem, since it happens even when almost no load is being pass through those relays?
So i have read what i can find on Victron's website about setting up the Auto gen start via the CCGX relays. I have an Onan that operates via a mom/off/mom(Start/off/Stop) switch. I saw the $80-$100 time delay relays that they reference and i understand their design but is there a better option for way to make the generator start and stop through the CCGX?
Hello, I have a Multiplus 2000/12/80. The Ground Relay setting is on by default. Based on my reading it looks like I should turn it off. I don't have a ground relay wire hooked up and I didn't buy an autotransformer. All I have hooked up to my multiplus is the battery, chassis ground, shore power, AC, and battery temperature cable. Am I missing anything or should this be turned off? Would having it turned on have caused any issues?
Thanks for the help!
So installing a few Multiplus II's in US/ split phase with an autotransformer. The manual lacks clarity here. On the Quattro you leave the "ground relay" box checked in VEconfig, flip the dip switch near the small terminals to "reroute" the signal to the external relay terminals. On the MPII there is no dip switch to "reroute" the control signals to the external terminals. Does the inverter sense an external relay and reroute on its own? Does disabling the ground relay in VEconfig enable the external terminals?
Whats the proper procedure on a MPII?
This device worked perfectly over the past two weeks and today it started dropping the AC loads.
This notification is displayed – “MultiPlus-II 48/5000/70-50 - #8 Ground relay test failed”
The VE.Bus Error report shows – “Last VE.Bus Error 11 report 0x24/Error occurred/GND Relay Error”
When I restart the Multi it produces the error right away. The bulk and absorption LEDs are also on.
Current firmware version is v471 (Multiplus II software version: 2623471)
I have done the following:
-Verified that AC-in GND is properly connected to grid earth.
-Tested for voltage between AC-in GND and AC-in Neutral. Ok - no voltage measured
-Verified that earth and neutral is not connected somewhere. All ok.
-Physically disconnected all cables from AC- out1 and AC-out2 to verify that there is no problems with any of the loads.
-Switched loads directly to grid via change over switches - all loads functions properly.
-Tested RCDs all ok.
I am trying to get some form of low voltage disconnect working utilising the BMV-702 relay (or CCGX for that matter....)
Importantly however i want to put a "delay" in place so that if i switch the kettle on and the voltage dips, it doesnt suddenly shut off power.
I have the relay set up as "inverted", so that it is normally closed.
I have the "minimum closed time" set to 1 minute; and
I have the Relay-Off delay set to one minute.
However as soon as the voltage dips below the trigger point, the rely instantly goes to Open.
Unfortunately i suspect that min closed time, is exactly that.....once the relay closes again it will take (in my case) 1 minute to go open again; I think the logic doesn't quite work when inverted.
At the moment i am using the relay on my multiplus, including programming the delay with the assistant. the trouble is that if i toggle the power on my multiplus, it then triggers the relay and trips the low voltage disconnect as well. Hence i am trying to use the BMV relay.
thanks in advance for everyone's thoughts!
We are designing and off grid system with a solar array though a couple of Smart MTTPs. There is almost certainly a Cerbo GX in the system. During the day when the SOC reaches 100% we would like to be able to send any further solar energy to a simple DC heater. This would need to switch out when the MTTP were no longer exceeding the normal system load.
We hoped to program the Cerbo relay to control a high power relay. Is this possible. Or is there another way. I noted the Cerbo info state "diverts excess (solar) power to self-consumption" but fail to find an explanation.
Many thanks for all contributions
I have a diesel generator which starts when the battery voltage is below a certain level which is triggered by Cerbo gx relay1. I would like to know if I can send any signal for low fuel reading examples under 5% or 20L to be sure the generator doesn't start if the fuel is too low.
We are trying to get the ACout 2 relay work as a deferrable Load controller, the issue we are facing is that we need the following condition to happen in AND not OR logic to activate our water-heater so we can make sure that we are
1- Not affecting the batteries absorption cycle by sucking current from it during Absorbution, which will be the case if we use ONLY a voltage set point.
2- Create a very narrow operation window for the deveriable load to work in
Is there any possibility to make a programmable relay logic conditions in AND not OR?
Edit: I changed the Digital Input Type from Door Sensor to Burglar Alarm. Some inputs send updates to VRM Portal on every poll and some send it on an event. With the Burglar Alarm type I can see the exact times my inverter switches ACOut2. Everything else in this guideline stays exactly the same. Note, the images have not been updated and still show the Door Sensor input type - used for reference only.
While I am also waiting on Victron to find time to add the ACOut2 Relay Status to VRM portal and the Modbus Registers I thought I'd use a workaround to get what I need.
The following is a workaround to get a Quattro ACOut2 Relay status on VRM portal and also to check it via Modbus/TCP. Below is what it will look like.
What you need:
1. GX device with Digital Inputs. Refer to the following link to compare different models.
2. Two to Six core Mains rated data cable depending on how many inputs you want to use, that you can legally use inside a distribution cabinet. I used some spare CBus Pink data cable that has an isolation voltage of 4KV. It has 4 cores but only used two for Digital Input 1 and Ground.
3. A suitable connector, to plug into your GX device's Digital Input port. I'm using a Venus GX and it requires a RJ12 connector. Refer to your GX device manual to see what is required.
4. A Mains rated DIN relay like a Hager EN146 Humfree relay.
Venus GX Setup
1. In your GX setup, go to Menu -> Settings -> I/O -> Digital Inputs and Enable Digital Input 1 and select Burglar Alarm.
2. Go back to the the Main Menu and you should see the Digital Input now visible on the GX screen. Go into the Digital Input 1 menu and select Setup. Make sure you Disable the Alarm notification and select Invert otherwise the state will show Alarm when in fact it's disconnected or unplugged.
3. Go one step back in the Menu and select Device. In this menu you can rename the input to EG. 'ACOut2 Relay'.
At this point the new Digital Input should be visible on VRM Portal under Devices.
To setup VRM Portal to show the status you need to go to Advanced and then select the Widgets icon in the top right hand corner. Scroll down to the new Digital Input and select the two options as per below.
You now have VRM Portal reporting on the Digital Input 1 you enabled.
1. To wire everything together you need to install the Relay coil between ACOut2 and Neutral after your ACOut2 breaker. The relay will engage when ACOut2 is active and disconnect when you are in EG. Inverting Mode or any other mode that disconnects your main ACOut2 Relay.
2. Wire the NO/COM contacts of the new relay back to the GX device's Digital Input 1 using the mains rated data cable and you are ready to roll.
I know this method is a workaround but at least you can monitor the state of the relay via VRM Portal as well as Modbus/TCP. In my particular case I wanted to know when it engages or not as I suspect a controller failure on my Quattro is not handling ACOut2 Relay as it should (fix in progress...)
To check the status of the relay using Modbus/TCP just connect to the GX IP address and use the Digital Input 1 ID and Register to read the Holding Register value. It should be either 6 or 7 as per the documentation.
I am not an electrician and any work done from the above suggestion is at your own risk and I am not responsible for any damage it might cause. If you feel you need verification or assistance with the above then please contact your Victron installer/reseller/distributor or electrician.
It would be useful to be able to change the state of a relay via VRM for example that could control a load remotely. IE - turn an airconditioner if it had been left on accidentially . At the moment a customer is using the relay in the MPPT to do this function but this is not ideal.
New to this so please bear with me.
Does anyone have any thoughts on configuring a gas alarm with solenoid shut off valve via the digital inputs and relay port on the Cerbo GX? I'm looking at a gas alarm setup (BEP Gas Detector) with two sensors and solenoid but its working out very expensive, £300+. Wondering if there may be a better way to use a simple gas detector and solenoid (gas rated) for this with the Cerbo GX?
I have a Off-Grid Quattro 10kVA with AC Connected 3kW Fronius Primo solar inverter and 4kW of solar panels. Frequency shift is used to manage battery overcharge. System works great in summer but we are expanding for winter with additional solar, and a wind turbine. We will AC connect an additional 4kW Fronius and solar array. For wind, we are installing a 3kW 60V AC turbine that will rectify to 48V DC and this feeds to a grid tie wind controller/ inverter (China Supply) that will synch to the AC Bus. The controller will dump power to dump resistors to protect the turbine from over speed/ voltage/ frequency.
However, i am concerned the Wind controller inverter will not spill turbine power (trigger dump resistors) when the AC Bus frequency is shifted by the Victron Quattro (High batrery voltage). Logic tells my the inverter would disconnect on high AC Bus frequency and send all power to dump resistors, though I cant be sure and manufacturer info is sketchy.
My question is whether it would be possible as a back-up to use one of the quattros Programmable relays to trigger when the AC Bus frequency is shifted to say 53hz. In this way I could trigger dump resistors to spill wind turbine power when it is not needed for House Load or battery charging.
My MultiPlus 2 GX is not discharging the batteries. According to the documentation, the ESS Relay Test is not completed. I have checked it in the settings, and indeed it is not done.
Can someone explain me please, what this Test does and how to start it?
If i choos "Ausgleich" the first option on the screenshot, it starts to charge the battery. Not regarding the state of charge not the max. allowes charge voltage. It's set to 56V and I charges even > 58V.
I'am worried, because my battery is 100% charged and discharge is not working at all. Any good idea how I can get this stupid test done?
Hi all, Im using a smart MPPT 150/70 connected to cerbo gx via ve port to monitor battery voltage via the VRM alarm rule. When voltage drops we get alarm email but the relay output on cerbo gx that is configured to alarm doesn't change status .
Also when i try config low battery as additional alarm rule in VRM via selected MPPT device comes up as per below:
Low batt. voltage alarm: No value available, product not connected?
Any help would be great cheers
One relay controls the generator start function based on SOC as reported by a SmartShunt. Turns ON the main generator at 60% SOC, and OFF at 90%. So far so good.
Is there a way to use the 2nd relay output with similar logic to control the field current to the main engine alternator so it turns ON at 80% and OFF at 95%?
Alternatively, I imagine I could use a BMV-712 and use its relay logic as the control for the second charging source as a function of SOC?
Greetings All , Question is . When using a Venus GX or Curbo GX . I need to activate one of the relays based off one of the Temp Sensors plugged in to the Venus or Curbo . I can get an alarm via the VRM as well as an email notification and that works fine but I need the relay on the Curbo to be activated . This is to enable a backup system for the refrigerator . Any advice would be great if this can be setup .
Hi Victron gurus. I have a weird problem:
I had installed a 15kVA using AC2 as the mains input and AC1 for generator (don't ask me what possessed me to do that) It worked fine although I wanted to use GX gen start/stop relay and prevent switching off of relay if mains was present (AC1 - I realized I couldn't change it to AC2)
So I rewired - gen to AC2 and mains to AC1, as it should be.
Immediately on turning on, after the brief monitor period of incoming mains a relay could be heard clicking on, a brief, normal hum of inverter, then click off, and repeat, non stop.
After some time having turned off mains, I tried it again and it clicked a bit but then came alive and ran fine for a few days.
Next I knew, my AC2 out relay was behaving badly. AC2 out powers a line that has 3 relays on it. The "1st" relay is on GX gen start stop, running 2x cold rooms. Was working like clockwork, next I hear the cold rooms were coming on and then going off after a short time.
Conditions: Relay off >12000Watts for 10sec, relay on <10000Watts for 30 sec. Load of 2x cold rooms is 2500Watts together. Off if SOC <90%, on if SOC >95%, don't "run gen" if AC1 is present. Battery was 98% SOC...
Tong test revealed 30 to 40Amps drawing on AC2 (6 other drinks fridges on same line). I am still suspicious that this is higher than normal - yet to double check.
Back to problem 1: I remotely sent updated settings, as I checked my parameters for AC2. The moment the inverter rebooted, my chap on site reported the return of the dreaded AC1 input clicking....
When mains is turned off the clicking stops.
System installed in a 3 phase building using one phase. Voltage sitting at 202Volts. No voltage fluctuation to speak of during the clicking event.
I tried changing to a different phase - same problem and same low 202Volts.
0.62V between neutral and ground on mains side.
Inverter output 2 pole isolators switched off - no difference (both AC1 and AC2 outs)
Am yet to try putting mains back to AC2 input, but this will be a fruitless exercise as it needs to work on AC1.
Any clues??? Is the inverter bust? If so howww?
I tried to attach audio but was told I can't attach such a file type................ Victron Community??
In my aplication i need detection of charging by MPPT. I was going to use the build in relay, but there is no such option. The perfect solution would be to trigger it when charging power is for example 50W or higher. As i saw in configuration its not posible to detect charging, so for sure its not posible to detect specific power of charging. Now im using Day detection option, but its also not working - if there is some not natural source of light its always trigered.
Summarizing i need to detect day of charging from MPPT, prefered without any other devices.
I've reviewed all the related posts here I can find but I still cannot figure out what I am doing wrong.
I want the BMV to operate a 12V relay as a low voltage cutoff. I want the relay to be normally open and only close and allow power to pass when the voltage is above cutoff value.
The contactor pulls just shy of 1A when it's closed.
I have a 48 to 12v dc-to-dc converter that i am using to power the contactor. I took the 12V positive with in-line 2A fuse and ran it to the "C" port of the BMV. I ran a wire out of the "NO" port to the plus side of the contactor. Ran a wire from the negative side of the contactor back to the negative bus.
I have also tried using the "NC" port instead.
I can get no response from the BMV. I have it set for Default mode and have toggled between the two "Invert" modes. I can hear something happen in the BMV but the contactor never actuates.
Anybody have an idea what I am doing wrong?
Hi! I tried to find this info in the documentation but couldn't.
If I have a relay assistant with multiple rules, does that trigger when any or all the conditions are met in the settings?
There’s no controllable relay on multiplus II Gx’s I can see the point of an all in one neat unit but the controllable relay is an important feature in so many installs? As it goes I’ve bought one for an install not realising till it was too late I thought it would have standard gx functionality and a controllable relay on board. Is there a way I can still operate a generator between certain percentages that are transmitted from canbus bms batteries I was thinking virtual switch maybe? Not ideal though.
Hello, is it possible to configure the output relays K1 and K2 so that they work at a given temperature? I get the temperature from a temperature sensor connected to CerboGX.
And one more question, how to display this temperature on the monitor?
I'am Installing a Multiplus II 48 5000 with solar MPPT Charger.
And now I'm wondering about the new Error 8 / 11 Report page, because there ist an Error listet an I don't know how to delete this error.
The system is running fine and I want to get rid of this error. What also confuses me is that the error main page shows no VE Bus errors at all. And this is where I need more information: Does last VE Bus error report mean the last error 8 or 11 is stored in this list and just stays there for ever?
to exclude any futher wiring mistakes I disconected all AC-Out wires inside the Multiplus.
Only AC-In is connectet and I checked the wires serval times.
As in many european Countries the N and PE on the AC-In are at Ground Potential, but this should not be a problem. I have a standart european TN-C-S Power Grid.
With this question I just want to make sure I'm not chasing any errors witch I solved long time ago.
Hope you can help me
I'd like the fans in my battery box to turn on during high temperature's. The VictronConnect app as an option under the Relay selection called High Temperature (Dimming) - When looking this up in the manuals the only information shared is:
High temperature (Dimming). This option switches the relay ON when the charger output current is reduced due to high temperatures. Use this option to for example switch an external fan.
Does anyone have information? At what temperature does it consider high temperature? What does the "dimming" mean? To be honest I'm a little disappointed at the lack of documentation on this relay options.
I need to use one relay for the Genset to switch ON when the battery bank (Pylontech) SOC goes down to 20% (lets say). and stop when the batteries get charged.
I also need a second relay for a device that needs to know the battery charge, ie that it will turn ON only when the batteries are full.It just needs the signal. How do I program this? In the comparisson table (https://www.victronenergy.com/live/venus-os:start#comparison_table) it says that the Cerbo has 2 x NO/NC.
Is this enough for what I need? (genset+the other device)
Thanks a lot
I assume the relay coil should be 48v, I want to control 12v 30A loads and can't find one. Any sources ?