MultiPlus 12/3000/120-50 120V (FW 418) with VE.BUS BMS
DMC 200 GX
BMV-712 Smart (v4.03)
I just added a DMC to a system that has been running 2+ years without one. The goal is to have the DMC allow a 1-30A adjusting range with the Multi defaulting to the lowest level
I lowered the input current limit in the MultiPlus (using VEConfig) from 9A down to 1A using VEConfig. I have verified that the MultiPlus is set to 1A after power off/on.
Regardless of what I do, the CCGX and DMC still thinks the current limit is 9A. I programmed the DMC for the upper 30A limit. The DMC works just fine adjusting the current limit >= 9A up to 30A. It just will not allow it to go lower than the old 9A setting.
I did try redetect system the Multi on the CCGX with no luck.
What's the magic to get the CCGX/DMC to see the new lower 1A setting in the Multiplus?