Configured everything last night successfully.
Got pylontech batteries (2) hooked up to a 3000/48 multi and a 150/70 mppt with the CCGX.
Everything works as expected, last night we used the inverter to power the home. Come morning I decided to connect the solar array to the mppt to start charging.
It seems to be working (early morning producing very little W) but as soon as I turn on the PV switch the information on the CCGX about the PV and batteries start to go in a connect disconnect cycle about every 5 seconds.
The data from the inverter works fine and the inverter as well but it just keeps connecting and disconnecting all the time.
It seems to be working fine but not sure if this is a bad sign,turned off pv just in case
Anyone seen this before, couldn't Google fu out of this one :(
[EDIT] Addition, found some posts with similar issues pointing to firmware versions. Seems I'm ok based on the Victron pylontech manual page:
CCGX is at v2.18 - docs say 2.15 minimum
Multiplus is at 430 - docs say 422 minimum
[Solved[ Turned out the bluesolar MPPT version wasn't good. Thanks for the help.
Updated to latest on CCGX which then triggered the warning on the version on the MPPT and through victron connect updating firmware was a breeze.