Hi . What happens if the mains supply to a 3 phase ( 3 x 5 KW) quattro loses a phase?
Does the whole system change onto battery, or will it continue charging off 2 phases and give a normal 3 phase output?
Attachments: Up to 8 attachments (including images) can be used with a maximum of 190.8 MiB each and 286.6 MiB total.
The whole system will switch to inverter mode.
Thanks Matthias. So in Inverter mode, will the 2 quattros that still have mains supply keep topping up the battery?
If all three are in inverter mode the quattros will be disconnected from the grid as described in this thread.
Parallel, split- and three phase VE.Bus systems manual
Theory on wiring large systems PDF
Three-phase and parallel system theory training presentation
Three-phase & Parallel installation training video
38 People are following this question.
1-Phase ESS on 3-Phase Grid with Phase Regulation: "Total of all phases", Error displaying correct consumption
ESS, AC PV, "Switch as group", why?
3 phase system and single phase MP
PV Inverter Assistant - unbalanced PV
#1 Device Switched Off momentary