Good day all,
I have a Multiplus 2 ESS system connected to a DB that has manual a transfer switch between generator and Utility. (Generator use is very little)
I recently had to use my backup generator to charge battery but was unable.
(I now know it was due to grid code etc.)
my question is why cant a user accessible function not be made that will change settings like LOM and weak ac, etc. when generator is selected or triggered via input to accept generator power and then when generator is off and grid back all settings will revert to grid settings?
also would it be an accepted approach to save different settings on VE configure (one Grid and one generator) and upload to multi if I need to use generator and the re upload to go back to grid?