Does 2 Pylontech 3.55kw Batteries have enough power to run a Multiplus II 48/5000 inverter charger?
No. The compatibility page recommends 4 but the model is rated for 25A.
While the system will work, you will be discharging them over their continuous amp out rating.
A 5kVA can pull at full rating 83.33A. so you need to make sure at minimum you have a pack that can do that. More if you are starting pumps and you know you may pop over the 4000W
I am assuming you are using the us3000C
Continuous Discharge Rate (Normal Use): 1776 W , so if you have 2 then your max load should never be above 3552W.
The pylontec is also limited in how fast it should also be charged as well.
I dont know how suppliers are on your side, but where we are if they see a mis-sized pack and loads to high for the battery the warranty is void.
47 People are following this question.