2 -Quattro - 10k inverters not accepting grid. Will start to load then disconnect.
Doesn’t drop or spike just disconnect.
Any help would be appreciated.
check to see if you are getting voltage sag as when they connect they would be charging the battery and thus drawing quite a bit of current and this maybe causing the incoming line voltage to sag down to the disconnect voltage. Try reducing you max charge rate and see if that stops the line voltage sage if thats occurring
38 People are following this question.