I have 9,9kW panels. 36pc 275W Voc38,7V Isc9,17A.
That's all for Off-grid:
Quattro 10000 48
Smart Solar MPPT 250/100
BYD Premium LVL 30,8kWh
So long as temperatures never caused the panels to exceed 250v the controller could handle it.
You would however be unable to use a lot of your solar capacity as that controller is only rated to 5800w @ 48v
I would consider adding another controller or reducing the number of panels. 24 panels (6s4p) would be the maximum I would connect to that controller.
23 People are following this question.