Does the gx read all the batteries?
In other words does it show all 7 online?
What is the system using for SOC in systen settings?
@Alexandra The Gx device it’s showing that 4 are online definitely these is one bank of the US3000c .
Then it is acomms issue.
So check cables. Are they all the same age/firmware?
Age and firmware sure they must be different since the other bank they’re the US3000 models.
Or I will stack them up to create a single bank and see the outcome.
The only difference between type A and type B is the ground.
But with the newer batteries as master that does not matter as the master is the one that passes on the info via can and the rest are connected internal comms not with Can.
You can stack them physically different but comms as one bank with the new batteries as master.
Sometimes you have to make your own cable with pins 1-3 blank(not connected.)
@Alexandra I will re crimp the other end and only use the pinout that I only need on the Can cable .Thanks
34 People are following this question.