How large a inverter would be necessary to run a 1000W single phase 230V motor?

Considering a multiplus 12/1600/70

Is that a sufficient size?

- Home
- Anonymous
- Sign in
- Create
- Spaces
- Grafana
- Node-Red
- Questions & Answers
- Modifications
- Communauté francophone
- Deutschsprachiger Bereich
- Preguntas en Español
- Explore
- Topics
- Questions
- Ideas
- Articles
- Badges

How large a inverter would be necessary to run a 1000W single phase 230V motor?

Considering a multiplus 12/1600/70

Is that a sufficient size?

Comment

1 Answer

You need to consider the starting current of the motor. A motor's starting current can be 5 or more times the running current for a few cycles which might cause the inverter to shut down due to overcurrent. Most meters won't measure this starting current/power so you need to look at the motors LRA (locked rotor amperage) spec to know what the starting current is (or measure it on a scope where the true current peak can be seen. The inverter's peak power spec needs to cover the LRA current.

Also, remember the number in the model number is volt-amps, not watts. A motor is probably not going to have a power factor of 1.0 so that needs to be taken into account as well.

Also, inverters produce less continuous power at higher temperatures.

**45** People are following this question.

Multiplus Compact 12/2000/50 Fuse Type not specified

firmware compatibility three phase system MultiGrid-II and MultiPlus-II

Leaving MultiPlus voltage sense connected when battery disconnect switch is OFF.

Multiplus Constant Battery Discharge Current without relaxation

Connecting Multiplus and Phoenix VE Direct inverters together?