How much current AC Out-2 on EasySolar II GX 3000/48 supports ?
i cant find this in the manual which only states that the Out-1 can supply up to 45A.
Can anyone help please ?
as the AC-Out-2 is in series to the AC-Out-1 and just appended with a switch/relais, the total of 45A will apply for the BOTH of the two outputs together, no matter where you draw the power.
well, yes. but I guess you know, that a 60A breaker will actually never trip - because the load wont ever rise that high (as it simply cannot) and so 'save' your used wires & loads.
nevertheless, it's good to have those breakers, no question. how about some breaker near the 45A ?
(45A actually already require 16mm² - is it even possible to connect such a cable to those outputs?)
Do you want to use ESS?
If yes it will probably not work with that ATS at the input, because in most cases the grid code you have to select will not accept the generator.
32 People are following this question.