I have a question regarding Multiplus 48/5000VA possible overload scenario.
My Multiplus should hande around 4500W continuous load, right. My hole house is behind this inverter, but I also have 16A grid connected to Multiplus, just in case.
My house is pretty small, so normally there is no problems to run the hole house with inverter and solar panels.
Now I have a plan install few heaters (Winter is coming)….
My question is:
If Multiplus output power is on the limit, let say close to 4500W, 16A grid is connected, and ESS is running with 20W grid setpoint, does Multiplus draw automatically from the grid more power, if total load goes over that 4500W limit …. Let say like close to 5000-5500 W ?
All load is connected to AC out 1, AC out 2 is not in use, and I want to keep it that way.
I have never tested overload scenario…. So that’s why my question…