I have some troubles to with the PLC connected to the CCGX. Can anyone help?
Attachments: Up to 8 attachments (including images) can be used with a maximum of 190.8 MiB each and 286.6 MiB total.
Maybe @mvader (Victron Energy) knows the answer on this one?
Hi, I don't know what is wanted to be queried here. And the query seems to query 434 addresses at once?
I'd start with single register queries, and make sure to super closely read the explanation about register numbers and unit ids in the Modbus TCP documentation:
Hope that helps!
Thank you @mvader (Victron Energy).
We are trying to write to «Active input current limit» at address 22.
With a scalefactor = 10, the typed qty 434 will be the same as about 43 Ampere per phase. This value will be changed depending in which generator that are online. Function code 6 = «Write singel register» in modbus. We will look closer at the register numbers and unit-IDs, as you have suggested.
We had incorrect unit-ID. It was set to 2 and the correct was 246. Now it works as it should.
18 People are following this question.
Quattro AC connections suggested manual update
Modbus TCP & Control of Cerbo GX/Quattro
viewing conditions options on ccgx via MODBUS
ModbusTCP. Cannot read majority of registers.
Can you configure your system with Modbus-TCP?