How do i get power from second ac out on my Multiplus 12/3000. Works fine otherwise.

- Home
- Anonymous
- Sign in
- Create
- Spaces
- Grafana
- Node-Red
- Unsupported topics
- Questions & Answers
- Modifications
- Communauté francophone
- Deutschsprachiger Bereich
- Preguntas en Español
- Explore
- Topics
- Questions
- Ideas
- Articles
- Badges

How do i get power from second ac out on my Multiplus 12/3000. Works fine otherwise.

Comment

1 Answer

the AC out 2 is only available when shore power/or gen set is connected.

*Two AC outputs*

*Besides the usual uninterruptable output (AC-out-1), an auxiliary output (AC-out-2) is available that disconnects its load in the event of battery operation. Example: an electric boiler that is allowed to operate only if the genset is running or shore power is available.** **After AC power becomes available on AC-in-1, the load on AC-out-2 will be reconnected with a delay of approximately 2 minutes. This to allow a genset to stabilise. **There are several applications for AC-out-2. Please enter “AC-out-2” in the search box on our website and find the latest information about other applications. *

**10** People are following this question.