How do i get power from second ac out on my Multiplus 12/3000. Works fine otherwise.
the AC out 2 is only available when shore power/or gen set is connected.
Two AC outputs
Besides the usual uninterruptable output (AC-out-1), an auxiliary output (AC-out-2) is available that disconnects its load in the event of battery operation. Example: an electric boiler that is allowed to operate only if the genset is running or shore power is available. After AC power becomes available on AC-in-1, the load on AC-out-2 will be reconnected with a delay of approximately 2 minutes. This to allow a genset to stabilise. There are several applications for AC-out-2. Please enter “AC-out-2” in the search box on our website and find the latest information about other applications.
10 People are following this question.