Can I extend the cable for smart bms cl 12/100 to multiplus by 0.5 metre. Also does it matter which colour (orange or yellow) is connected to the load disconnect?
Attachments: Up to 8 attachments (including images) can be used with a maximum of 190.8 MiB each and 286.6 MiB total.
Finally got a response back from Victron! The orange lead goes to the load disconnect and the yellow to charge disconnect. Yes the lead can be extended on the multiplus side.
32 People are following this question.
Multiplus shore power pass through
Inverter Product line
MultiPlus shuts down while on shore power after bulk charge is complete
Multiplus 48/3000 ESS reliability
MultiPlus current reading incorrect