Hi, I need to install 3phase system without neutral 220VAC, is possible to make this configuration with 3 multiplus?
I understand to make this configuration with 3 multilplus 120VAC, but What do I do with the neutral?
It is not possible to make a Delta configuration. Only Wye. It is because without a neutral, the inverter has no reference point with which to regulate its output Voltage.
The only way I can think of is to use a Wye / Delta transformer after the inverters.
5 People are following this question.