Got issues with a pair of 5k Multis (single phase setup) and a 6KVA genny (Mecalite alternator) off grid
on off on off on off - pass through - charging - power assist etc.etc.
Charge rate is way below the shore power limit. (its like it doesnt have time to ramp up) - Or starts off about what would be expected - then quickly drops off.
Batterys charge current limit is unchanged at 125A (Pylons) - No other sources of generation at the time.
Dynamic Curent limiter is enabled - UPS is Disabled
Accept wide Range - enabled
Power Assist standard 2.0 Boost factor
Generator frequency tends to be up around 52HZ - but is a bit all over the place.
I am of a mind to fit a 250w heater to the output of the generator to help stabilise the voltage and frequency prior to the Multis connecting.